recently we were called out to a vital piece of equipment, system was alarming on low pressure fault.
We quickly diagnosed that the system had lost its gas. After reclaiming the remaining gas left in system we added OFN and set about finding our leak.
We found the leak on a low pressure filter dryer, leak was fixed and re tested.
system was vaced out to remove any moisture in system and re charged with R410A.
System left fully operational with minimal down time.
Call Sub-Zero: 02920290693